PAT TESTING BERKSHIRE | SURREY | LONDON
PAT Testing Berkshire
What is involved in PAT Testing?
If you are looking for a quick guide to what’s required as part of your PAT Testing inspection, then you are in the right place.
The NICEIC Technical Helpline recieves hundreds of calls each year and here is some of the top questions covered in our easy PAT Testing Guide.
The NICEIC technical helpline gets hundreds of calls each year about the requirements for the inspection and testing of electrical appliances or PAT Testing.
PAT Testing is covered by three activities:
- User checks
- Engineer checks:
- Formal visual inspections (without tests)
- Combined inspections & tests
Most faults or damage can be found just by looking. Users should be encouraged to look critically at the electrical equipment in their own working environment. Staff should be given straightforward training and instruction on how to carry out a simple visual check before using any electrical appliance.
After disconnecting, the signs to look out for on the equipment, cable
- Damage, such as cuts or abrasions to the cable covering
- Damage to the plug such as the casing is cracked or the pins are bent
- Non-proprietary joints, including
taped, in the cable
- The outer covering of the cable not being gripped where it enters the plug or equipment. Look to see if the
colouredinsulation of the internal wires is showing
- Equipment that has been used in conditions where it is not suitable, such as a wet or dusty workplace
- Damage to the outer cover of the equipment or obvious loose parts or screws
- Overheating (burn marks)
Checks should be undertaken when the equipment is taken into use and during use. Any faults should be reported to the management and the equipment
This type of inspection does not require the use of any specialist test equipment as it is purely
The inspection should
- The cord grip is holding the outer part of the cable tightly
- The wires, including the earth wire where fitted, are attached to the correct terminals
- No bare wire is visible other than at the terminals
- The terminal screws are tight
- There is no sign of internal damage, overheating, dust or dirt
- This visual inspection should not include taking the equipment itself apart since this will take a lot more time, could damage the equipment and may be dangerous.
Combined Inspections & Tests
The checks carried out as above will have identified most (but not all) potentially dangerous faults – some deterioration of the cable, its terminals and the equipment itself can be expected after significant use. Equipment may also be misused or abused to the extent that it may give rise to danger; this is why PAT Testing is so essential.
PAT Testing, together with a thorough visual inspection can detect faults such as loss of earth integrity like a broken earth wire within a flexible cable, or deterioration of insulation integrity or contamination of internal or external surfaces.
Competent staff should be instructed to carry out inspections and tests, using a proprietary appliance testing instrument, as stated in the IEE Code of Practice for In-service Inspection and Testing of Electrical Equipment (The PAT Testing regulations. They should have sound knowledge and experience relevant
We also offer general guidance for appliance testing in non-specialised situations such as Offices, Hotels, Rented Accommodation
The IEE Code of Practice for In-Service Inspection & Testing of Electrical Equipment give comprehensive information on the frequency of inspection and testing of equipment, such as:
Note+: For some equipment such as children’s rides, a daily check may be necessary by supervisory, teacher or member of staff.
What type of equipment is covered in the PAT Testing regulations?
The following types of electrical equipment are covered:
Portable Appliances – An appliance of less than 18kg in mass that is intended to be moved while in operation, or an appliance which can easily be
Moveable Equipment – This is equipment which is either 18kg or less and not fixed such as electric fire, or equipment with wheels or other means to facilitate movement, such as an air conditioning unit.
Handheld Appliances – This is portable equipment intended to be held in the hand during normal use, such as hair dryer, drill, soldering iron.
Stationary Equipment – This equipment has a mass exceeding 18kg and is not provided with a carrying handle, such as a refrigerator, washing machine.
Fixed Equipment – This is equipment which is fastened to a support or otherwise secured in a specified location, such as a bathroom heater, towel rail.
IT Equipment – IT equipment includes electrical business equipment such as computers and mains powered telecommunications equipment, and other equipment for general business use.
Looking for more advice on
PAT Testing for your business?
testimonals | PAT Testing Berkshire
Our customers say about working with ESI: Electrical Safety Inspections
“We would like to
Some three hundred items were tested in two days with
We will most certainly retain your services on an ongoing basis.”
“An engineer from ESI recently came to Nuclear Industry Association to test all our electrical equipment.
The testing was done swiftly and professionally and caused little to no disruptions to our normal working day.
I can highly recommend them.”Kate Amos